Brown cartons(outside) 530*330*220mm
Ningbo or Shanghai
NEW floor heating thermostat 16A :
underfloor heating thermostat
heating digital thermostat
electric thermostat for floor heating
high quanlity with competitive price TUV CE and OEM/OEM
Large LCD digital thermostat 85-250 VAC / 24VAC ( option)
C15.GH1 Current 3A C15.GH3 Current 16A
Electric thermostat for floor heating or hot water radiator heating systems
C15 Heating thermostat with LCD screen, which has manual mode or programmable.
The thermostat is recommended for the control of electric heating device
or on/off valve actuator in hydronic underfloor heating.
Basic function: 1. Recommended for control of underfloor heating and electrical heating. 2. Electronic on/off control up to 3600W, 16A or 6000W, 30A 3. Setting daily 4 periods of programmable, time settings, Kinds of periods of time modes. 5+2 / 6+1 / 7days
4. Large Back-lit display, LED screen, easy-to-see and read
5. Infrared remote-controlled function(option) 6. Built-in interrupter 7. Two work mode switchover: ( programmable ,non programmable) 8. Display temperature recalibrates 9. Low temperature protection function 10. Surveys, display and set room temperature 11. Memory function: Parameters are permanently held in memory and retained during power outages 12. Anti-freezing protection 13.2-sensor: Built-in Room sensor , floor limiter sensor ( floor limiter sensor is option)
Product Specifications: Voltage: 110(± 10%)VAC / 220(± 10%, -15%)VAC, 50/60Hz 24VAC ( option) Differential Temperature: 1 ° C Max Setting Temperature Range: 5° C~35° C
External Limitation: 5°C~60°C( factory setting 35°C) Mounting: Mounts directly onto wall or wall-box Temperature range: 0° C - 40 ° C Sensor type: NTC Color: White ivory Relative humidity: < 85% (23 ° C)
Housing material: anti-flammable PC
Dimensions: 86mm× 86mm× 13mm(H/W/D)
Dimension in mm
Step 1: Separate the Polycarbonate Bezel unit from the LCD screen. A: Hook B: Buckle
Step 2: In Laka buckle, outside at the same time lift up the movement, it is necessary to separate the iron with the movement.
Step 3: Fixing plate with screws to the wall to ensure that the de-energized state product back wiring diagram connected electrical lines.
Combinations: Align the four hooks, press down on the movement, the iron plate with movement combinations, and then fasten the frame